Yesterday, I had to wire up a new Vaillant Ecotec 800 series boiler which has the pump contained in the boiler housing and also has a cylinder overheat thermostat. All the external controls are in the airing cupboard directly above.
I have had to modify the Sundial S-plan wiring diagram a little bit to incorporate the overheat stat and the permanent live to the boiler.
This is the new layout of the 10-way wiring station - [ATTACH]1555[/ATTACH].
I would be grateful if one of my more learned colleagues would cast an eye over it for errors. If the diagram is correct, it can be moved to the downloads section for the benefit of others.
Welcome to Talk Electrician Forum
|Welcome to Talk Electrician Forum, the UK's Friendliest Electrical forum on the internet, whilst you can view all our posts and topics like most online communities you must register to post (reply, or ask a question) in our community, but don't worry this is a simple free process that requires minimal information for you to signup. We do have different membership levels (called silver and gold) as a subscription service, BUT, this is an extra, and not needed, So please feel free to join for FREE, and then decide if you like our community, and would perhaps like to subscribe to any of our our extra services. Our members offer the best advice in the electrical industry including DIY,Domestic,Commercial,Industrial,Renewables,Health and Safety issues and Control and Automation.
Be a part of Talk Electrician Forum by signing in or creating an account.
Guest Message by DevFuse
S-plan with pump overrun wiring diagram
No replies to this topic
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users