Welcome to Talk Electrician Forum
|Welcome to Talk Electrician Forum, the UK's Friendliest Electrical forum on the internet, whilst you can view all our posts and topics like most online communities you must register to post (reply, or ask a question) in our community, but don't worry this is a simple free process that requires minimal information for you to signup. We do have different membership levels (called silver and gold) as a subscription service, BUT, this is an extra, and not needed, So please feel free to join for FREE, and then decide if you like our community, and would perhaps like to subscribe to any of our our extra services. Our members offer the best advice in the electrical industry including DIY,Domestic,Commercial,Industrial,Renewables,Health and Safety issues and Control and Automation.
Be a part of Talk Electrician Forum by signing in or creating an account.
3 Phase Time Switch
Posted 25 March 2011 - 08:32 AM
I'm just about to install a 3 phase 8 Way DB that will feed 4 x 9Kw 3 phase immersion elements.
The customer has asked for each element to be fitted with a time switch.
The elements will be controlled by a 20amp Rotary Isolation switch.
What can I install, and where should it be installed?
The elements are due to be hard wired, but I suppose I could fit a 32amp plug onto the tail?
Posted 25 March 2011 - 10:48 AM
Posted 25 March 2011 - 12:15 PM
Posted 01 May 2011 - 09:38 PM
OK, the plan has changed!
There can be a single timeswitch to control power from main isolator to DB.
What is available out there, that can handle this load?
It also needs to have a manual override to stich the timeswitch off!
Posted 01 May 2011 - 09:59 PM
That way you have to reset it in the event of a power fail.
IF it MUST come back on after a power fail, then use a latching switch in the door?
Just wire the controls for the 4 contactors in parallel feeding each one from the DB?
Put a local isolator at each immersion if the control panel is remote?
Really you need to be able to isolate the panel, though with 4 circuits scrap that!...
Use one timer fed from another db way to run 4 seperate boards similar to the suggestion above?
You could put the timer control in a small enclosure in an accesible area, or even use a domestic timer as you would be just controlling the contactors, then use a box like the suggestion by Benji for each heater just leaving out the timer?
Not really now sure what you are trying to achieve!
It feels tooo late now, don;t know why very tired all of a sudden!
Posted 01 May 2011 - 11:00 PM
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users