Welcome to Talk Electrician Forum
|Welcome to Talk Electrician Forum, the UK's Friendliest Electrical forum on the internet, whilst you can view all our posts and topics like most online communities you must register to post (reply, or ask a question) in our community, but don't worry this is a simple free process that requires minimal information for you to signup. We do have different membership levels (called silver and gold) as a subscription service, BUT, this is an extra, and not needed, So please feel free to join for FREE, and then decide if you like our community, and would perhaps like to subscribe to any of our our extra services. Our members offer the best advice in the electrical industry including DIY,Domestic,Commercial,Industrial,Renewables,Health and Safety issues and Control and Automation.
Be a part of Talk Electrician Forum by signing in or creating an account.
List IN ORDER- test required for a new installation
Posted 31 May 2011 - 01:35 PM
As I am doing more on revision for the big exam in 301-302-303. using loads of information , books, internet , old revision sample papers and even in the forum...
There is a question that confused me of which one is the right answer..
According to my notes in the course that the list IN ORDER the test required for the new installation is..
1) Continuity of earthing conductors
* main bond
* Equipotential earthing
2) Continuity of ring final circuit
3) Insulation resistance
NOTED that all sensitive equipment must be turn off or unplugged.
4) Polarity test ( -+)
FIRST 4 IS ALL DURING DEAD TEST
** AND FOR LIVE TEST
5) Earth electrode test ( Ze ) only for TT
6) Earth loop Impedance test ( Zs)
7) Prospective fault current ( PFC)
*PEFC ( between Phase and earth )
*PSCC ( between Phase and neutral )
8) Functioanl test
* RCD 1/2 x - 1 x and 5 X
Could anyone please correct me if there is missing or in a wrong order .. I have seen different sequence of testing in new installation... my notes might be in wrong order or maybe your expertise will add more knowledge to me and to the other members in this forum.
Thank you all .
Posted 31 May 2011 - 02:04 PM
Posted 31 May 2011 - 02:19 PM
Posted 31 May 2011 - 02:38 PM
1 Do you need to put polarity in your live tests as well as dead? You need to make sure you have the correct polarity coming into the installation.
2 Don't forget the test button on your RCD test.
Posted 31 May 2011 - 02:47 PM
Posted 31 May 2011 - 03:31 PM
Polarity is the first of your 'live' tests - it applies to the polarity of the supply.....which you would want to confirm, along with Ze, before you energise the installation.
Posted 01 June 2011 - 12:25 AM
Page 33 Guidance Note3
Para 2.7.4 "The sequence of Tests"
will answer your questions!
Or PIR testing...
page 73 GN3!
Posted 06 June 2011 - 07:29 PM
best thing to do is make an Excel file like I have to show the sequence, expected results, how you do it, settings used, leads used etc.
0 user(s) are reading this topic
0 members, 0 guests, 0 anonymous users